Reticulated Gas System a a mechanism of supplying uninterrupted gas horn a centralized cylinder storage bank to the end user's point through the pipe line. The Gas is supplied from a centralized cylinder bank or bulk storage fealty installed within the premises. This will be differentiated in three form
Reticulated Piped Gas System is supply of Liquefied Petroleum Gas (LPG) through a network of pipelines, from a centralized cylinder bank / manifold system or a Bulk Installation (Bullet) to customer (end user’s) kitchen / Bath room / Heating Appliances.
This is achieved by reducing the Storage Pressure to appliance pressure by means of suitable Pressure regulators with the extreme safety. Thanks to the Automatic Change Over Regulator for ensuring the continues gas supply to the end user even the service cylinder bank gets Exhausted. Special regulators like under pressure shut off (UPSO) and over pressure shut off (OPSO) incorporated in the system to ensure safety to the end users. Reticulated Pipe Gas System is supply of Liquefied Petroleum Gas (LPG) through a network of pipelines, from a centralized cylinder bank manifold system to customer (end user’s) kitchen. We follow the proven and latest regulatory system which inculcates a sturdy - 3 Stage Pressure Regulation System (PRS) to provide multilevel safety
PRS - I reduces cylinder pressure from 6 bar to 1 bar*
PRS - II reduces Pressure from 1 bar to 110 millibar*
PRS - III reduces pressure from 110millibar to 28 Milli bar*
PRS - I.
PRS-I is installed in the Gas Bank, wherein the cylinder pressure reduces from 6 bar to 1 bar Gas Bank includes 2 Cylinder Manifolds
Each manifold with battery of cylinders connected together parallel to a common pipe line. When the Active Manifold is empty, then supply of gas will automatically commence from the Standby Manifold using Automatic Change Over Regulator which ensures continues gas supply. An OPSO (Over Pressure Shut-off) Valve is a safety device which monitors the gas supply pressure & compares it to its preset level. In case the regulator fails at its preset level, the OPSO valve will automatically active there by gas supply will be shutoff. Advanced leak detection system shall be provided at gas bank for extra precautionary measure.
PRS - II.
PRS-II (with UPSO & OPSO) is installed near the building structure at basement or Stilt level, wherein the pressure is further reduced from 1 bar to 110 milli bar. This low pressure gas passes through HEADER & RISER pipes and enters to each individual consumer’s flat. It has safety features such as UPSO (Under Pressure Shut-off) & OPSO (Over Pressure Shut-off)
UPSO- If the pressure on the outlet falls below set limit due to leakage, then the regulator shut-off the supply of gas
OPSO- If the pressure in the outlet of PRS-| increases from the cylinder bank, then the regulator shut-off the supply of gas
PRS - III.
PRS – III (with UPSO) is mounted just before the gas meter of each individual flat. It further reduces the pressure from 110 milli bar to 28 milli bar, thus the pipe connecting the gas stove receives the pressure of 28 milli bar.
UPSO - The regulator will instantly shut-off the supply to the Gas stove in case of an interruption of LPG gas flow for some reason while
cooking or in case the customer has left the gas burner on without attending to it even after gas supply starts. To get the normal supply again, the customer should close the Gas Stove burner & wait for 1-2 minutes. Thus the combination of safety devices eliminates the risk of LPG leaking into the customer’s kitchen and creating a potential hazard.
OUR DESIGN & INSTALLATION SYSTEMS CONFIRMS TO
Gas Cylinder rules 2004
Why Reticulated gas system?.
There are about 25 million households using LPG and as many as 13 million are on the waiting list. The average growth rate in demand has been 12 to 13 percent and is expected to be of the same order in the years to come. However, there are restrictions by way of domestic availability. Lack of infrastructural facilities and shortage of gas has hampered the growth of the Petroleum Gas Companies. Today the public sector units are in no position to increase their bottling capacity. Today’s situation warrants an alternative system and Reticulated Gas System, being used in Europe and America, is the best solution to this problem. Reticulated gas system is Tailor made to suit the project requirements. This centralized distribution system supplies gas to each and every user through a network of absolutely safe system and is the best alternative to the conventional LPG distribution system. The rigours of getting a refill are totally eliminated and the consumer ‘pays for what the uses.
PNG systems are restricted to certain to geographical areas and further the availability of natural gas is questioned everywhere. LPG systems have limited loops; hence more security and more control on the safety aspects. At every stage, state-of-the-art equipment is used with Carbon steel pipes, to provide the best and safest LPG Reticulated System. The system is tested as per strict norms of the Oil Industry at every stage. Because safety is foremost followed by Convenience.
Reticulation system provides continuous supply of gas at the turn of tap.
No need to wait for the new cylinder after exhausting the existing cylinder.
Space saving in the Kitchen.
Improves the aesthetic sense of the Kitchen.
More Safety to the kitchen as Under/Over Pressure Shut off Regulator is incorporated.
No need of blocking the money as well as the space for the second cylinder.